Expansion Tank Replacement
Skip Ahead to Topic
- 1 Expansion Tank Services
- 2 Expansion Tank Replacement
- 2.1 Does every home in Frisco has to have an expansion tank?
- 2.2 Mandatory pressure reducing valve installation in Frisco
- 2.3 Results of a broken Pressure Reducing Valve
- 2.4 Plumbing Code in Frisco for Pressure Reducing Valve
- 2.5 Process to a Pressure Reducing Valve
- 2.6 Is there a reason for putting the PRV the flower bed?
- 2.7 Replacing floating expansion tank
- 2.8 Trident Plumbing
Does every home in Frisco has to have an expansion tank?
Every home 2002 or has one, and they typically last eight to 12 years, some people get 15 to 20, but the average lifespan is about 12 years. If your home was built before 2002, you probably have high water pressure, but you don’t have that regulator. The city didn’t realize it was an issue until ’02 and in ’02 they made it mandatory that all the builders put them in. So there are homes in Frisco area that are ’98 models, ’99 that have very high water pressure and they don’t have this set up with the pressure reducing valve and expansion tank.
Mandatory pressure reducing valve installation in Frisco
What happened was in ’02 the city made it ordinance that says all homes built 2002 and newer going on have to have this pressure reducing valve in the flower bed, or some people have them inside, but most of them are in the flower bed. In 2008 is when they realized you had to have the expansion tank to go with it. So there are homes in the ’05 range that have this that do not have this, but when you put in a pressure reducing valve, what you’re doing is called closing the loop. The water comes from the city at 110 psi and leaves at 60 psi. When you have that regulator installed, 60 psi can never push back on 110. The 110 is stronger. That’s why you need the expansion tank, a place to take that excess pressure.
Results of a broken Pressure Reducing Valve
Basically it’s premature wear on all of your appliances, any appenditures that attached to the cold water system, washing machines, dish washers, refrigerators, toilet fill valves are typically the first to go. You can get humming, banging, knocking in the walls. I’ve had calls where people say they think they have ghosts in their pipes from the different noises that the house is making. So this little device can cause the house to do weird things. That’s the pressure reducing valve. There’s a lot of city codes that go with putting this in. It’s got to have a 12′ X 18′ yard box, which is sitting behind you. It’s got to have gravel put in the box. It’s got to be raised to the top of the box with a shut off valve prior to a union, so basically this isn’t the one going in there. This isn’t the one, this is going in the attic, but basically if the arrow was going forward, you have to have a shut off valve prior to the regulator and it can not be deep down in the dirt. It has to be raised up to right under the lid of the box. So this particular home, it’s about three feet deep so this is a really deep one.
Plumbing Code in Frisco for Pressure Reducing Valve
Plumbing code in Frisco says that you can have your water line at a minimum of 12 inches deep. This home here is at about 36 inches so it’s just going to be a little bit more of excavation required, but what we’ll do is we’ll raise it to the top of that box, so that way in the future if this ever has to get swapped out again, 10-12 years from now, we won’t have to re-excavate that deep down into the ground.
Process to a Pressure Reducing Valve
Transcription from video – This one’s about three feet. Two,three feet. So you’ve got to dig this whole thing out. We have to dig it out and get about six inches below the water line that’s in there currently. There are tons of roots, because I had to remove all those trees already because they grew right over the top of the box.
Is there a reason for putting the PRV the flower bed?
Just that’s what they want. Each municipality can interpret the code however they want it. So just to hide it a little bit I guess? Yeah, I’m assuming so, or so that there’s no damage inside the house. It’s all outside if it leaks. It feeds the flowers if it leaks and then you don’t know.
How many PRV replacement jobs have you done in Frisco?
In Frisco, hundreds. Yeah and the newest code that Frisco just did is you have to put a union on it now. They changed that within the past, you know, six months to a year. That used to not be code, but now you need a union on it. Whether it’s in the wall or in the ground, used to, unions had to be in the walls, not under dirt.
Replacing floating expansion tank
We’ve got a two gallon which is made for one heater, we have two heaters so this needs to be double the size. It’s over the attic so if it ever leaks it’s going to come straight down into his ceiling.
We’re going to move the new one over here above this pan and then it’s all welded together so we’re going to replace all of this. These heat traps, nobody uses these anymore. They’re not really outlawed, it’s just theories have changed over the years so being that there’s a welded on cup link and it’s all rough, we’re going to go ahead and cut all that out and start over. We’re just going to do it right the first time so that way, I mean, Lee’s not going to stay here, but whoever gets to live here doesn’t have to keep paying to do the same service over and over and over again.
This thing really is twice the size of that other older one.
So know what we’ll do is this. Step one, cut the water line. So this sucker is heavy and full of water, so it’s going to drop when I cut this and probably going to lose a little bit of water, so I try to be as quick as I can.
The very last step after this is just to come up and insulate once we check everything for leaks.